|Place of Origin:||China|
|Minimum Order Quantity:||1|
|Delivery Time:||5-8 word days|
|Payment Terms:||L/C, T/T|
|Rated Voltage:||48V||Rated Speed:||4000RPM|
Resemble Ebm-past 133mm DC Centrifugal Fan With Fresh Air System Eqjipment Cooling
EC Motor – Principle
With an EC motor the electronic circuitry stands in lieu of the traditional mechanical commutation meaning the right amount is being supplied in the right direction at exactly the right time providing precise motor control.
Permanent-magnet brushless DC motor within the rotor
The stator is driven by electronic switches (which replace the Carbon brushes), controlled by a microcontroller.
Electronic system (hall effect sensor or software is used to recognize the rotor position)
AC operated (230Volts Single phase or 380/480Volts 3phase, 50/60Hz)
Energy savings with EC fans
Let’s assume a laminar flow workstation requiring 13200m³/h at 450Pa. This requires 4 off Ø315 backward curved fans. Now let us assume that this workstation operates for 50 weeks of the year and for 8 hours per day at full speed. During non working hours to maintain the work area, the fans are run at roughly half the airflow.
AC fan 2800hrs @ 4 x 1.41kW = 5.64kW 15,792 kWh
5600hrs @ 4 x 0.62kW = 2.48kW 13,888 kWh
Total A 29,680 kWh
EC fan 2800 hrs @ 4 x 1.04kW = 4.16kW 11,648 kWh
5600 hrs @ 4 x 0.27kW = 1.08kW 6,048 kWh
Total B 17,696 kWh
A minus B 11,984kWh saved with the EC fan
Why choose us?
1. We belongs to the factory, so price we can give is based on factory cost, not trading cost.
2. We are sole International sales of the factory, we can help to control and protect the market of clients.
3. We integrates different kinds of products for air management.
4. We are independent of factory. This make us standing in the position of client instead of factories. It will solve your problem of communication with factory.
Contact Person: walter